Australian Standard For Building In Bushfire Prone Areas (AS3959) Explained.
Summary of our mesh products compliance with AS 3959-2018.
Australia has a long history of bushfires endangering properties all across the country. Protecting existing, established homes from the onset of bushfire attacks was and still is the responsibility of the owner or occupier. In more recent times the state fire authorities have published recommendations for how to best prepare for bushfire attacks and all of them indentify the importance of ensuring the roof guttering systems are clear and free of leaf litter and debris. Some state fire authorities go a step further and also suggest that "quality metal leaf guards" be fitted.
For many years these recommendations were the only place gutter or leaf guards were mentioned.
When things began to change was in the late 1990’s. Regions which were identified to be at an increased level of risk of bushfire attack were deemed to be “Bushfire Prone Areas”. Recommendations were heard regarding the potential benefits of addressing bushfires at a construction and design level and in 1999 The Australian Standard for building in bushfire prone areas (AS3959-1999) was released. This standard indentified five (5) risk levels of bushfire attack and included 3 separate construction levels. These construction levels placed specific requirements on the building products to be used in the construction of any new dwelling (or major renovation of an existing dwelling). The only reference to gutter guard in this standard stated;
“Any device used to stop leaves collecting in the gutters shall have a flammability index of not greater than 5 when tested in accordance with AS 1530.2.”
In March of 2009 a third edition of AS3959 was released and superseded AS3959-1999. AS3959-2009 incorporated a few changes including the method of determining the Bushfire Attack Level (BAL) for a site, and now comprised six categories, namely BAL-LOW, BAL-12.5, BAL-19, BAL-29, BAL-40 and BAL-FZ (flame zone).
These six categories determine what construction and design requirements are placed on any new construction or renovation, to be undertaken in areas identified as bushfire prone.
In November 2018 a new standard was released making AS3959-2018 the current Australian Standard for which gutter guard needs to comply with.
In addition to the requirements of The Australian Standard For Building In Bushfire Prone Areas, relevant local councils and state fire authorities may also add conditions as part of development applications (DA) for construction or land subdivisions.
What demands on gutter guard does the current Australian Standard (AS 3959-2018) make ?
The Australian Standard for building in a bushfire prone area (AS3959-2018) places only one restriction on gutter guard regardless of the Bushfire Attack Level (BAL). (see extract below)
“If installed, gutter and valley leaf guards shall be non-combustible”
To determine if a material is non-combustible it must be tested in accordance with AS 1530.1. However any product which has a paint coating over a metal base would not pass AS 1530.1, as that small amount of combustible material would be enough to fail the test. There is a clause in the Building Code of Australia (BCA) that allows finishes of less than 1 mm thickness over metal substrates, provided the finished product achieves a ‘Spread of Flame index’ not greater than 0 when tested to AS/NZS 1530.3.
Our aluminium guttermesh has been tested in accordance with AS 1530.3 and achieved a spread of flame index of 0 (test result available on request) and for the purpose of compliance therefore deemed “non combustible”
It is important to note that the individual states of Australia may impose their own additional requirements.
What is ember guard and what are the ember guard requirements ?
Ember guards are designed to create a barrier to restrict burning embers from gaining access into a home via any small gaps which were previously not addressed.
The specification on ember guards does change as the BAL increase. At the highest BAL (BAL F-Z or Flame Zone) AS-3959-2009 calls for “ember guards made of non-combustible material or a mesh or perforated sheet with a maximum aperture of 2 mm, made of corrosion-resistant steel or bronze”,
It is important to note that ember guard can be made from non-combustible material or a mesh or perforated sheet with a maximum aperture of 2 mm, made of corrosion-resistant steel or bronze".
One of the most common areas we are asked to supply ember guard for is to address the underside of roof corrugations. However the Australian Standard extract below identifies several other methods of addressing this area also ;
8.6.3 Sheet roofs
Sheet roofs shall—
(a) be fully sarked in accordance with Clause 8.6.2, except that foil-backed insulation blankets may be installed over the battens;
(b) have any gaps sealed at the fascia or wall line hips and ridges by -
(i) a mesh or perforated sheet that confirms with Clause 3.6 and that is made of corrosion-resistant steel or bronze; or
(ii) mineral wool; or
(iii) other non-combustible material; or
(iv) a combination of any of Items (i), (ii) or (iii) above.